The Sense system identified and tagged my Well pump. After monitoring the Power meter, there were two things that stood out. The signature contained a spike on start, which wasn’t always the same. Like a bounce was occurring on a relay contact. The second thing that I noticed was the Well Pump was coming on way to much. It was short cycling. Like, two flushes of a toilet activated the pump to run.
Reviewed the well pump connections, etc. Replaced the $25 relay control switch and the faulty pressure gauge on the well manifold. Adjusted the Well Bladder. This fixed the short cycle and inconsistent spike displayed by the power meter.
This may have saved an expensive well pump replacement!